- Posted by enmet
- On October 31, 2017
- 0 Comments
Fixed Gas Monitoring Sensors for Ambient Air Proper Selection and Placement
The health and safety of personnel working in a potentially hazardous environment is an important concern for all employers. There are several key factors when assessing the need for ENMET’s fixed gas detection systems when monitoring ambient air. First, identify the toxic or combustible chemicals/gases/vapors that could be present and creating hazardous conditions in the area. Once these hazards are identified, important characteristics of each hazard can be obtained to help with proper selection and placement of ENMET’s fixed gas detection sensor transmitters and monitoring systems. These important characteristics include:
- TWA (time-weighted average)
- IDLH (immediately dangerous to life and health) value
- LEL (lower explosive limit) value
- UEL (upper explosive limit) value
- Density of chemical versus density of air (helps determine where to mount sensors)
Once this information is obtained, ENMET’s Sales Team can help you determine which of our fixed gas monitoring systems will work best for your application. The detailed information will also be useful in determining which sensors should be used, span calibration values and alarm point settings, and proper sensor placement (near ceiling, near floor or in the breathing zone).
Our laminated pocket size guide is a great tool that helps provide these answers for some of the most common toxic and combustible chemicals. Contact our ENMET Sales Team today for your free copy!
Come see us at the Air Quality Measurement
Methods and Technology Conference
November 7-9, 2017, Long Beach, CA
Be sure to visit ENMET at the Air Quality Measurement Methods and Technology conference. We will be featuring our new GC based product that offers a cost effective approach to benzene trace level detection. Stop by and check out our eGC, an innovative, next-generation fenceline benzene monitoring system. We will have experienced sales staff on hand to explain the amazing technology of the eGC which offers an affordable solution for determining the source, magnitude and timing of a benzene release at the fenceline.